Yes. In certain applications it may be desirable or necessary to use non-sensing leader cable between a ProReact Analogue control unit and the detection cable. This may be required if the expected ambient temperature range, or other environmental conditions, where the Analogue LHD cable is to be used is greater than the maximum ambient temperature range for the control unit.
The maximum length of leader cable that can be used per ProReact Analogue LHD system is 250 metres. Thermocable can manufacture and supply leader cable that is compatible with its ProReact Analogue LHD cable. Please contact us or refer to the installation manual if you require further information.